Universal Environmental Technology (UET) and its partners around the world are constantly installing new systems and developing new solutions for ecological water treatment.
Here are some recent updates.
A large cooling tower is used at a local cement plant to cool water in a steam condenser. After 15-months of CHEMICAL-FREE operation, the UET technology REDUCED the effluent BLOW-DOWN by nearly 100%.
In each UET system, the supply water passes through a series of reaction chambers, which are configured to apply partial-electrolysis in order to restore the supply water’s mineral balance to an optimum equilibrium.
By applying DC voltage to electrodes in the chambers, H+ and OH- ions are produced by partial-electrolysis. The addition of OH- ions promotes scale formation on the wall of the UET chambers. We are currently removing more than 500kg of scale and excess minerals per month.
#ChemicalFree #ScaleRemover #500kgPerMonth
UET is almost ready to ship 2 fully containerized systems that will be installed in a coal gasification plant in western China to solve scale problems in the water circuit, allieviate concerns of ash in grey water, replace chemical additives, and reduce water blow-down. The two containers together will treat 600m3/h.
UET recently took third place at an industrial innovation competition amongst select companies that participated in the final round during an innovation seminar.
We congratulate the entire UET team for their efforts to bring more awareness to its sustainable and environmentally friendly solution in the field of industrial water treatment!
A bio-tech company in Brazil is now enjoying the benefits of UET’s Chem-Free CT treatment, which is expected to raise the cycles of concentration from 13 to 30. This will not only save the company significant amounts of money, but will also help relieve the recently experienced water shortages, which is good for everyone!
Yet another successful UET installation (bottom right), in this case to treat a cooling tower in Turkey (left), to prevent the formation of scale, corrosion and bio-contamination, all without additive chemicals!
See project details below:
Basin – 1300 m3
CT circulation pumps – 12
Cooling flow rate – 3176 m3/h
Water quality –
4000 μS conductivity of make-up water.
450 ppm of total hardness.
900 ppm of carbonate hardness.
70 ppm of silica
External heat exchangers – 4
R&D heat exchanger connected on site – 1
Temperature sensors on each line
Cooling water DeltaT – 2
Process water DeltaT 10
UET circulation – 800 m3/h
Dedicated UET pumps – 3
Water pressure – 1.5 Bar
Communication to all units through Backsoft
8 UET 4×4 unit